Starbucks says they plan to start reopening many of its company-owned locations with modifications starting Monday amid the COVID-19 pandemic. Starbucks had temporarily closed half of its 8,000 US company-owned stores. The company plans to have 90% of its locations reopened by early June. Starbucks CEO Kevin Johnson is optimistic that customers will return and is taking a very cautious and methodical approach to safely re-opening stores. In communities where there are higher COVID-19 casualties, Starbucks won’t “turn the dial up,” Johnson noted. Instead, the chain will maintain drive-thrus, mobile order with contactless pickup, and curbside service where there are parking lot facilities, he added. “But in other communities where we see the number of COVID cases continue to decline, we might now open our cafe for limited seating. We might have a to-go model. And so we’re going to be in this phase where we’re tuning the store protocols and what we offer customers as we monitor the situation community by community,” Johnson added.
Re-opening your Restaurant or Food Service Facility? If you are an owner operator and have been shut down for an extended period of time, Pentair Everpure has the following guidance for your water treatment system;
Filtration systems are designed to be operated on a continuous basis with only relatively short periods of down time (overnight and holidays). When a system is shut down for an extended period of time, there is a potential for microbiologic growth. To address concerns with system operation after the shutdown, please follow the below instructions. This is applicable to all Pentair filtration systems (i.e., pre-filters, carbon-based cartridges and Reverse Osmosis (RO) systems).
Periodic Flushing In cases where the customer knows that the system will be down for an extended time and is able to get to the system on a periodic basis, follow the below flushing procedure every 3-4 days:
Flush the system for a minimum of 5 minutes by letting the outlet water run to the drain. For systems with multiple outlet ports, flush for a minimum of 5 minutes through all ports.
Empty the tank through the outlet port until the pump turns on. Once the pump is on, flush the system for 10 minutes by letting the outlet water run to the drain. For systems with multiple outlet ports, flush through all ports.
Shutdown for Less Than or Equal to 7 Days:
When you put the system back into operation, flush the system for a minimum of 5 minutes by letting the outlet water run to the drain and then proceed with normal operations. For the systems with multiple outlet ports, flush for a minimum of 5 minutes through all ports.
When you put the system back into operation, empty the tank through the outlet port until the pump turns on. Once the pump is on, flush the system for 10 minutes by letting the outlet water run to the drain and then proceed with normal operations. For the systems with multiple outlet ports, flush for a minimum of 10 minutes through all ports.
Shutdown for Greater Than 7 Days:
All Systems (Filtration and RO)
Remove all existing filtration elements that are present in the system (pre-filters, carbon filters &/or RO cartridges) and dispose. Disinfect the system as instructed in the applicable Installation and Operations Guide for that specific system.
After the disinfection process is complete, replace the filtration elements with all new pre-filters, carbon filters &/or RO cartridges. Flush the system as instructed in the applicable IO Guide to complete the procedure.
Initiate a manual regeneration.
Shutdown for Greater Than 30 Days:
Disinfect per the Installation and Operation Guide for that specific unit. Generally speaking, it is adding some bleach to the brine tank before initiating a manual regeneration.
Pentair assumes the following in providing this guidance: Incoming water is potable.
There is no boil-water advisory or boil-water order issued by the applicable public health or governmental authority.
System is being maintained within normal operating temperature and other conditions as set forth in the applicable specification sheet.
If you have concerns or cannot confirm these assumptions for the system, follow the instructions above under the section entitled “Shutdown for Greater Than 7 Days”.
For more information or questions regarding your Pentair Everpure Water Treatment system please email us at firstname.lastname@example.org or call us directly at 800-942-7873